Home > Industrial > Design Requirements
There are three different applications of ionization equipment within an industrial facility.
For corrosion control, and depending on the level contamination within the space (G1-GX conditions), 10-20% of the room volume is necessary for the recirculation system. For example, a room that is 20’x25’x10’ (5,000 ft3) with G3 or GX conditions would require 20% (or 12 ACH) of recirculation air or 1000 CFM. The same room with G1 or G2 conditions would require 10% (6 ACH) or 500 CFM.
Odor control applications are different in that we must apply highly ionized outside ambient air to the space. Please click on this link to bring you to Odor Control Design Requirements.
Office and common areas will typically have much less contamination and therefore, sizing the proper equipment for these areas is typically determined by the existing HVAC equipment and their related airflows.